Relay Settings for 113/135 Series for Standard & Dynamic ADR
Relay Off Delay
When the output control is PID (Proportional) with a set point relays are set to trip when the measured variable exceeds the Upper Set Point Limit. The relay will remain ON until the measured variable drops below the Lower Set Point Limit.
The can be configured to remain ON for 1-32767 seconds after it drops below the Lower Set Point Limit. See Relay Config / Relay Deadband Off sec. in GRIDview. Each time the measured variable again exceeds the Upper Set Point Limit then drops below the Lower Set Point Limit the timer will zero and begin the countdown all over again.
By setting the delay to the maximum setting of 32767 which equates to more than 9 hours will cause the relay to remain ON after the first trip for the duration of the Event.